Level regulator minimum-maximum with pump activation and solenoid valve. In addiction resistance management and security time out
Loading cycle of a boiler with time-out and double level probe (minimum/maximum):
The loading function regulates and controls the correct level of water in the boiler.
The pump and solenoid valve output are activated whenever the minimum level probe is not covered by water and they remain activated until the maximum level probe is reached by water.
The loading function remains activated for a maximum of 150 seconds (so called time-out). After this period of time the pump and solenoid valve outputs are deactivated in order to protect the machine from eventual breaks or malfunctioning.
Both an acoustic alarm and a LED indicate the malfunctioning.
In addition to the regulation of the pump, also the resistance is managed: it is activated if the minimum level probe is covered and deactivated if not. If the time-out period expires also the resistance is switched off.
Security management of the resistance:
If there is no water in the boiler, the activation of the boiler’s resistance may cause damage. This function deactivates the resistance when the level probe is not covered by water.
The user can customize the time of the deactivation of the resistance.